In many cases, several sensors are connected together to control the same fixture, or to trigger on each other, the sudden on/off may cause huge magnetic pulse and mis-trigger the sensor. Hytronik condominium sensor HC019V is specially designed for these applications with 1-10V output which employes a strong software to overcome the megnatic interferences.
In a lot of buildings, there is a need that the moving object in corridor or undercover garage can trigger a transmitter luminarie with connected receiver luminaries from more than one direction. Every transmitter luminaries (containing the sensor) should be able to trigger the whole installation whether it’s an on/off or dimming installation.
See the example below that there are several exits /entrances to the corridor, no matter which sensor at exit /entrance is triggered, the luminaries in the group will light up.
|Load ratings||800W – Capacitiv Load|
|2000W – Resisitv Load|
|Sensor Priciple||High Frequency (Microwave)|
|Operation frequency||5.8GHz +/-75MHz|
|Detection Range||Max. (OxH): 12m x 6m|
|Detection Angel||30 ~ 150 Degrees|
|Sensitivity||10% / 50% 75% / 100%|
|Hold time||5s/30s/1min/5min/10min/20min/30min, can be customized|
|Daylight treeshold||2~50Lux, disable, can be customize|
|Stand-by period||0s ~ 1h, +∞ (Selecteble)|
|Stand-by dimminglevel||5% / 10% / 20% / 50%|
|Operation temperature||-35 ~ +70 Degree Celcius|
|Certicication||Semko, CB, EMC, CE, R&TTE, SAA|